BCAB #977 - Combustion Air, Article 220.127.116.11.
February 22, 1988
Re: Combustion Air, Article 18.104.22.168.
With reference to your letter of January 28, 1988, regarding the application of Article 22.214.171.124. from the B.C. Building Code.
The house in question is new, built under the provisions of the 1985 B.C. Building Code. Under the circumstances we consider Article 126.96.36.199. to be applicable, requiring a ducted supply of combustion air from the outside, terminating at or near the wood stove.
We do not consider a window, in any location, as an acceptable equivalent for the provision of combustion air. The window, if open, will supply ventilation air for a room; the purpose of Article 188.8.131.52. is to supply combustion air direct to the appliance, regardless of windows, without the necessity for drawing warm air from the room for this purpose.
J.C. Currie, Chair