BCAB #969 - Exterior Exit Stairs and Fire Alarm for Motel, Sentences 220.127.116.11.(6) and; 18.104.22.168.(3)
January 26, 1988
Re: Exterior Exit Stairs and Fire Alarm for Motel, Sentences 22.214.171.124.(6) and; 126.96.36.199.(3)
With reference to your letter of December 24, 1987, regarding exiting. Our decisions on the two questions raised are:
1. We are dealing with an exterior passageway served by an exit stair at each end, so Sentence 188.8.131.52.(6) applies. This does not require that the stairs be enclosed, and provides exemption from the provisions of Sentence 184.108.40.206.(1), which contains the fire separation requirements between an exit and the remainder of the building.
On this issue, while we understand the concern of the authority having jurisdiction, we are unable to take the provision of the 1980 Code as requiring that these stairs be enclosed and fire separated. The situation is addressed more effectively in the 1985 Code, but those provisions cannot be applied retroactively.
2. We consider the building to comply with the provisions of Sentence 220.127.116.11.(3), and thus exempt from the mandatory fire alarm requirement.
J.C. Currie, Chair