BCAB #963 - Untested Wood Stove, Article 188.8.131.52.
January 26, 1988
Re: Untested Wood Stove, Article 184.108.40.206.
With reference to your letter of November 18, 1987 regarding acceptance of a wood burning stove.
This type of appliance is dealt with under Subsection 9.34.2. of the Code, and Article 220.127.116.11. requires that it conform to ULC-S627/CSA B366.2, "Standard for Space Heaters for Use with Solid Fuel". The Code merely requires conformance with the standard, not testing and listing by a fire testing laboratory, but the authority having jurisdiction would need proof of conformance with the standard.
From your letter it would seem that you have been asked to provide proof of conformance, and on this issue we are unable to assist. It may be that the Inspector will accept confirmation from the manufacturer that the unit conforms to the standard, or alternatively a site inspection by an engineer qualified in this particular field, although the testing required by the standard would be virtually impossible. Basically you should supply adequate proof that the unit either conforms to the standard, or is capable of being considered as an equivalent under the provisions of Article 18.104.22.168. of the Code. We can only you reapproach the inspection authority.
J.C. Currie, Chair