BCAB #731 - Fire Hose Connection Size, Sentences 188.8.131.52.(1) & (2)
November 30, 1983
Re: Fire Hose Connection Size, Sentences 184.108.40.206.(1) & (2)
With reference to your letter of October 25, 1983, regarding hose connections.
The Building in question is twelve storeys in height, and falls under the provisions of Sentences 220.127.116.11.(1) and (2). The Code requires 21/2 in. hose connections, this is mandatory. The reference to 11/2 in. connections does not apply to this building in view of the height.
This issue was raised under Appeal No. 611, which would clearly seem to deal with this situation.
J.C. Currie, Chair