BCAB #1780 - Attachment of Wood Shingles over a Capillary Break
March 17, 2016
Re: Attachment of Wood Shingles over a Capillary Break, Clause 22.214.171.124.(1)(b) & Sentence 126.96.36.199.(1)
The project is an addition to a single family house required to conform to Part 9 of the 2012 BC Building Code. The cladding proposed is cedar shingles and is attached to code compliant sheathing.
Reason for Appeal
The appellant is proposing to use a proprietary roll type product to create the required capillary break behind the cladding. Because of the use of this product, the building official has determined that the attachment of cladding does not comply with Sentence 188.8.131.52.(1).
The appellant considers that the proprietary product meets the requirements of Clause 184.108.40.206.(1)(b) for “an open drainage material, not less than 9.5 mm thick and with a cross-sectional area that is not less than 80% open”. The use of this product is permitted as a prescriptive solution under Part 9 of the Code and does not require the use of Part 5 or the code’s Letters of Assurance. The cladding is proposed to be attached to sheathing of a minimum thickness that complies with Sentence 220.127.116.11.(3), and fastened in accordance with Article 18.104.22.168 and Table 22.214.171.124.
Local Authority’s Position
The building official maintains that, although the product in question is a minimum of 9.5mm thick and is 80% open as required by 126.96.36.199.(1)(b), its other properties as part of a cladding system have not been evaluated. The code’s assumptions of compression, contact and friction are no longer present when a medium is introduced between the cladding and the supporting element in order to create a capillary break. The fasteners in the code have been specified based on the shank being fully supported. With the introduction of an intervening material in the capillary break, it is no longer known if the fastener lengths specified are appropriate. Due to the foregoing, the attachment of cladding does not comply with Sentence 188.8.131.52.(1). It is further unknown how this assembly will perform its intended function over time.
Appeal Board Decision #1780
It is the determination of the Board that the attachment of cladding, including wood shingles, to sheathing conforming to Article 184.108.40.206. through an acceptable intervening material providing a capillary break and conforming to Clause 220.127.116.11.(1)(b) and Sentence 18.104.22.168.(1) is compliant.
This decision is limited to the attachment of cladding through the intervening material and does not include the approval of the intervening material itself. In addition to the requirements of 22.214.171.124.(1)(b), the intervening material must also comply with Sentence 126.96.36.199.(1) of Division A and Article 188.8.131.52. of Division C.
Professional design and review (Letters of Assurance) have not been considered in this appeal.
Reasons for Decision
This decision is consistent with Appeal #1690.
The code does not specify direct attachment of cladding is required (without an intervening material).
Requirements for Letters of Assurance are not identified on the application form or in correspondence with the building official.
Lyle Kuhnert, Chair, Building Code Appeal Board