BCAB #1710 - Installation of Disinfection Device in Care Facility, Section 7.4, Drainage Systems
March 27, 2012
Re: Installation of Disinfection Device in Care Facility, Section 7.4, Drainage Systems
The appeal concerns the installation of seven bedpan disinfectors in an existing care facility. Six of the units discharge via an S-trap into drainage pipes in the floor while one unit discharges through a P-trap into drainage pipes in a wall. After a wash cycle a blower forces air at about 0.7 psi into the cleaning chamber. A pressure relief line connects to the drainage system downstream of the trap through a check valve to stop sewer gas from entering the unit, and ultimately the building, when the wash chamber isn’t pressurized.
Reason for Appeal
Sentence 188.8.131.52.(1) requires every fixture to be protected by a separate trap. Article 184.108.40.206. regulates the location of vent pipes relative to the fixtures they serve.
The appellant contends the Code does not specifically cover the installation of the appliance in question in a controlled environment such as a hospital. There is no reference in Table 220.127.116.11. to a bed pan disinfector or similar device. The check valve is integral to the appliance, is tested for at least 40,000 cycles and maintains an adequate seal from sewer gases. As for the S-trap the appellant contends that the integral component of the appliance is designed to prevent it from being emptied from siphoning action and the water level in the trap is clearly visible at all times to confirm this.
Building Official's Position
The building official maintains that, in accordance with Sentence 18.104.22.168.(1), the air discharge pipe from the device must be protected with a trap, not a check valve. Also, the building official maintains the units employing an S-trap do not meet the conditions described in Clause 22.214.171.124.(1)(b) regarding the total fall permitted on a trap arm.
Appeal Board Decision #1710
It is the determination of the Board that the proprietary bed pan disinfector is a fixture as defined by the BC Building Code and must conform to all applicable requirements for fixtures, including Sentence 126.96.36.199.(1) requiring protection by a separate trap and clause 188.8.131.52.(1)(b) regarding total fall permitted on a trap arm.
Ed MacKinnon, Vice Chair