BCAB #1661 - Travel Distance in a Residential Occupancy
June 17, 2009
Re: Travel Distance in a Residential Occupancy
The subject building is a 21 storey hotel tower in a larger resort complex which includes a casino, retail shops, restaurants, day lodge, amenity spaces and a residential tower. The building is sprinklered and the hotel floors comprise typical hotel suites on both sides of a 1 hr fire rated public corridor served by exit stair shafts near each end.
Reason for Appeal
Clause 126.96.36.199.(1)(c) permits a travel distance of up to 45 metres to at least one exit in a sprinklered floor area. Sentence 188.8.131.52.(1) describes travel distance as being measured along the path of travel from any point in a floor area to an exit except as permitted by Sentence 184.108.40.206.(2). Sentence (2) allows the travel distance to be measured from a suite egress door to the nearest exit where the suite is fire separated from the remainder of the floor area and the public corridor conforms to Article 220.127.116.11.
The appellant contends that the 45 metre travel distance can be measured from the suite egress door because the conditions in Subclauses 18.104.22.168.(2)(a)(ii) and 22.214.171.124.(2)(b)(iii) have been satisfied. In addition, since public corridors in residential occupancies must have a fire resistance rating, regardless of the presence of sprinklers, the building will exceed the requirements of Sentence 126.96.36.199.(2).
Building Official's Position
The Building Official contends that in order to measure the travel distance from the suite egress door Clauses 188.8.131.52.(2)(a) and (b) must be complied with. The building cannot comply with Subclause 184.108.40.206.(2)(a)(ii) so it cannot conform to Sentence 220.127.116.11.(2) and by default must comply with Sentence 18.104.22.168.(1) requiring the travel distance to be measured from the most remote location in the floor area.
Appeal Board Decision #1661
It is the determination of the Board that the travel distance can be measured from the egress door of the suite to the exit. The Code establishes minimum requirements, with Sentence 22.214.171.124.(2) indicating any fire separation in a sprinklered building would meet the minimum criteria. The Board considers the intent statement for this Sentence supports this determination.
George Humphrey, Chair