BCAB #1565 - Sprinklers in a Garbage Room, Sentances 22.214.171.124.(2), 126.96.36.199.(4) & 188.8.131.52.(1)
April 18, 2002
Re: Sprinklers in a Garbage Room, Sentances 184.108.40.206.(2), 220.127.116.11.(4) & 18.104.22.168.(1)
The project in question is a new unsprinklered building with retail use on the ground floor and residential occupancy above. An enclosed garbage room is proposed rather than exterior "dumpsters."
Reason for Appeal
Article 22.214.171.124. requires rooms for the storage of combustible refuse to be sprinklered. Sentence 126.96.36.199.(2) requires automatic sprinkler systems to "notify the fire department" when they are activated. Sentence 188.8.131.52.(4) permits water for fewer than 9 sprinklers to be supplied by the building’s domestic water supply. Sentence 184.108.40.206.(1) permits backflow prevention from sprinkler systems through the use of an alarm check valve.
The appellant contends that neither monitoring nor backflow prevention is required for the two sprinklers installed to protect the garbage room. The permission in the code for the two sprinklers to be tapped into the domestic water system results in these sprinklers being part of the plumbing system, not a stand-alone sprinkler system. Therefore, Sentences 220.127.116.11.(2) and 18.104.22.168.(1) do not apply.
Building Official's Position
The building official maintains that the garbage room sprinklers do constitute a sprinkler system intended for fire protection. Therefore, the sprinkler system must be connected to the fire alarm system such that activation of the sprinklers would notify the fire department. There is also a requirement to protect the domestic water system from the sprinkler system by a backflow prevention device.
Appeal Board Decision #1565
It is the determination of the Board that the two sprinkler heads do not constitute a system as intended by the code and Sentence 22.214.171.124.(6) exempts the need for fire department notification for a "local group of sprinklers." As the two heads are not considered to be a system, Sentence 126.96.36.199.(1) does not apply either.
George Humphrey, Chair