BCAB #1476 - Exit Through a Lobby, Articles 22.214.171.124. and 126.96.36.199
January 21, 1999
Re: Exit Through a Lobby, Articles 188.8.131.52. and 184.108.40.206
The project in question is a one storey sprinklered building of Group A Division 2 major occupancy. The main floor is equally divided into a meeting room and licensed beverage establishment with office and washrooms. The basement is mostly storage as well as two offices. Two exit stairs lead up from the basement to discharge at ground level. One leads through the main entry lobby while the other discharges into a short corridor leading from the main floor meeting room to the exterior exit doors.
Reason for Appeal
Sentence 220.127.116.11.(1) requires every exit to be separated from each adjacent floor area by a minimum 45 min. fire separation except as permitted by Sentence 18.104.22.168.(2). One exit from a floor area is permitted by Sentence 22.214.171.124.(2) to pass through a lobby provided certain conditions are met. Subclause (e)(ii) permits the fire separation between the lobby and most adjacent occupancies, including those of Group A Division 2, to be eliminated if the lobby and adjacent occupancies are sprinklered.
The appellant contends that both stairs from the basement can pass through lobbies that are not fire separated from the main floor. Fire rated doors are not required between the meeting room and the short corridor leading to the exterior into which stair #2 discharges.
Building Official's Position
The building official maintains that Stair #2 must be fire separated from the main floor by a 45 min. wall and a 20 min. door assembly. Stair #1 leads through a lobby conforming to Sentence 126.96.36.199.(2) at the front of the building and as only one exit from a floor area can lead through an exit, Stair #2 must exit directly to the exterior without passing through a lobby and must be fire separated from the main floor.
Appeal Board Decision #1476
It is the determination of the Board that exit stair #2 from the basement must be fire separated from the main floor. All the doors in this fire separation must have a 20 minute fire protection rating. Sentence 188.8.131.52.(2) permits only one exit from a floor area to pass through a lobby. The other exit from the basement (stair #1) already passes through the main lobby so Article 184.108.40.206. cannot be applied to exit stair#2.
George R. Humphrey, Chair