BCAB #1420 - Mezzanine Design, Sentence 126.96.36.199.(3)
July 17, 1996
Re: Mezzanine Design, Sentence 188.8.131.52.(3)
The project is an existing building with two small mezzanines which were constructed without a building permit. The open floor space in which the mezzanines are located is approximately 3718 square feet. One mezzanine is 487 square feet and the other is 518 square feet. A full height wall, not directly associated with either mezzanine obstructs some of the view of the open floor space from the larger mezzanine.
Reason for Appeal
Sentence 184.108.40.206.(3) permits a mezzanine to be excluded from the calculation of building height provided:
not less than 60 per cent of the horizontal plane separating the mezzanine from the floor space in which it is located is open,
except from within enclosures described in Clause (c), the mezzanine to a height of not less than 2150 mm above the mezzanine floor, is visually open to the floor space below except for guards not more than 1070 mm in height, columns and posts, and
not more than 10 per cent of the area above the horizontal plane is enclosed, except as provided in Sentence 220.127.116.11.(2).
First of all the appellant has determined that approximately 73% of the horizontal plane is open (the mezzanines occupy a total of 27% of the open floor space). The appellant then shows that each mezzanine has an open area, or areas, in front of it that corresponds to the requirement for 60% of the horizontal plane to be open. The two open areas associated with the larger mezzanine are separated by the full height view obstructing wall. The appellant argues that a line joining the two ends of this L shaped wall creates a triangular area approximately 7.5% of the open floor space and this is less than the 10% which is permitted by Clause 18.104.22.168.(3)(c).
Building Official's Position
The application form indicates the building official considers the design to contravene Clause 22.214.171.124.(3)(a) but no further comments were received.
Appeal Board Decision #1420
It is the determination of the Board that mezzanine #2 does not conform to Sentence 126.96.36.199.(3) for either of two reasons.
The Board considers the full height wall defines the open space in which this mezzanine is located. Therefore, less than 60% of the horizontal plane associated with this mezzanine is open. The full height wall is a visual obstruction which contravenes Clause 188.8.131.52.(3)(b).
George R. Humphrey, Chair