BCAB #1419 - Exit Trough Lobby, Sentence 18.104.22.168.(2)
July 17, 1996
Re: Exit Trough Lobby, Sentence 22.214.171.124.(2)
The project in question involves a new suite of Group A Division 2 occupancy in an existing building. A single exit is provided from a series of second storey rooms. This exit discharges through the lobby on the ground floor.
Reason for Appeal
Sentence 126.96.36.199.(2) permits "Not more than one exit from a floor area..." to pass through a lobby provided a number of conditions are met.
The appellant contends that all conditions of Sentence 188.8.131.52.(2) have been complied with and the design meets the requirements of the code.
Building Official's Position
The building official maintains that Sentence 184.108.40.206.(2) can only be applied where there is more than one exit from the floor area. As the portion of the floor area in question has access to only one exit that exit can not lead through the ground floor lobby.
Appeal Board Decision #1419
It is the determination of the Board that the exit from a floor area served by only one exit in conformance with Sentence 220.127.116.11.(2) is permitted to pass through a lobby in conformance Sentence 18.104.22.168.(2).
George R. Humphrey, Chair