BCAB #1377 - Egress from Residential Suite, Sentences 220.127.116.11.(5), 18.104.22.168.(1) & 22.214.171.124.(2).
January 18, 1994
Re: Egress from Residential Suite, Sentences 126.96.36.199.(5), 188.8.131.52.(1) & 184.108.40.206.(2).
The project in question is a high rise residential condominium required to comply with Subsection 3.2.6. There are two suites per floor except on the sixth storey which has only one suite. As there is only one suite on the sixth floor there is no public corridor and both the exit stairs and the elevator open directly into the suite.
Reason for Appeal
Sentence 220.127.116.11.(5) states that in residential buildings not more than 3 storeys in building height a dwelling unit is permitted to open directly into an exit stairway provided it has a second and separate means of egress. Sentence 18.104.22.168.(1) requires every floor area to at least two exits. Sentence 22.214.171.124.(2) requires elevator shafts containing fire fighter's elevators to be separated from the adjacent floor area by a fire separation with a fire resistance rating equal to that of the floor assemblies through which it passes.
The appellant contends that Article 126.96.36.199. focuses on egress requirements for multi-storey dwelling units and Sentence 188.8.131.52.(5) does not apply to this single storey dwelling. The floor area containing the single dwelling unit is provided with two exits in conformance with Sentence 184.108.40.206.(1). The fire fighter's elevator complies with the fire separation requirements of Sentence 220.127.116.11.(2) and with Sentence 18.104.22.168.(3) regarding the operation of the elevator door and is not required to be protected by a vestibule.
Building Official's Position
The building official maintains that Sentence 22.214.171.124.(5) is not limited to multi-storey dwelling units and allows a suite to open directly into an exit stair only in buildings of 3 storeys or less in building height. By placing a vestibule between the dwelling and the exit stair the dwelling no longer opens "directly" into the exit.
Appeal Board Decision #1377
It is the determination of the Board that the design in question is acceptable. A firefighter's elevator is not required to open into a vestibule provided the opening is protected by a closure conforming to Clause 126.96.36.199.(3)(a). The Board interprets Sentence 188.8.131.52.(5) as an exception to Sentence 184.108.40.206.(8) which is only applicable where there is more than one suite in a floor area. There is only one suite on the floor area in question. Therefore, it is permissible to open the suite directly into an exit stair as is common in other occupancies.
George R. Humphrey, Chair