BCAB #1237 - Indoor Miniature Golf - Article 188.8.131.52., Major Occupancy Classification
February 22, 1991
Re: Indoor Miniature Golf - Article 184.108.40.206., Major Occupancy Classification
A miniature golf business set up inside an existing warehouse building. The area in question is approximately 10,200 square feet and 22 feet high. The existing fire separation between this space and the adjacent suite has a fire resistance rating of 1 hour.
Reason for Appeal
The building officials have classified the miniature golf business as a Group A Division 2 major occupancy and Sentence 220.127.116.11.(1) requires a 2 hour fire separation between such an occupancy and an adjoining Group F Division 2 major occupancy.
The appellant does not feel the occupancy should be defined as assembly because the occupant load would never exceed 2 persons per 1000 square feet.
Building Official's Position
The building official considers the indoor miniature golf to be a Group A Division 2 occupancy as do other officials with whom he has checked. A 2 hour fire separation is required between a Group A Division 2 occupancy and the Group F Division 2 furniture manufacturer next door.
Appeal Board Decision #1237
The Board considers that indoor miniature golf is clearly an assembly occupancy classified as Group A Division 2 under Subsection 3.1.2. of the Code. Article 18.104.22.168. requires different major occupancies to be separated from each other by a fire separation with a fire resistance rating conforming to Table 3.1.3.A. This table requires a 2 hour fire separation between a Group A Division 2 major occupancy and a Group F Division 2 major occupancy such as a furniture manufacturing plant.
George R. Humphrey, Chair