Shipping Container Fire Safety
The purpose of this bulletin is to provide
- Owners with the British Columbia Fire Code (BCFC) requirements for confined spaces, such as shipping containers, being used for the storage of fuel fired equipment, containers of flammable liquids, or explosives.
- Emergency response personnel information regarding their safe conduct when working around metal shipping containers, and similar confined spaces where flammable liquids, or explosives, are stored.
In December 2011 a Fire Officer was fatally injured as the result of an explosion in a metal storage container (Sea Can). The storage container was being used for general storage purposes, which included gasoline-fuel fired tools and approximately one litre of methyl hydrate.
The locked container was exposed to direct fire impingement and radiant heat on three sides, caused by a burning wood frame building. As a result of that heat, some of the combustible material inside ignited. At the same time, the fuel tank(s) on gasoline-fuel fired tools allowed gasoline vapor to escape into the confined space. The requisite fuel-to-air mixture was eventually achieved and was ignited. The explosion caused both doors to disengage, sending them approximately 40 meters from the storage container. One of the doors hit a Fire Officer, causing fatal injuries. The explosion occurred an estimated two hours after the arrival of fire department resources.
The fire investigators concluded that the amount of flammable liquids stored in this storage unit was well within the amount permitted by the BCFC. In this incident extenuating factors led to the catastrophic failure of the container. Two of those factors were:
- Extreme external heating of a non-combustible closed storage container;
- Structural characteristics that initially contained the explosion until the weakest part of the unit failed.
These structures can pose a unique and previously unidentified risk to fire service personnel when responding to fires where metal storage containers (Sea Cans) are present. It is recognised that these containers are used extensively throughout the province and under most circumstances do not represent significant issues. However in some circumstances special precautions should be considered by responding fire personnel when the potential for an explosion exists or may exist.
BC Fire Code Requirements
Storage of Flammable/Combustible liquids for Incidental Use in Ancillary Outdoor Enclosures
- A fire safety plan developed in cooperation with local fire department is required in all buildings and open areas where flammable/combustible liquids are stored, handled, or used. [BCFC, Div. B, 220.127.116.11.]
- Ventilation of an enclosed space is required to conform to BCFC, Div. B, 18.104.22.168. if open containers are stored.
- Ventilation of an enclosed space is not required if Class 1 flammable liquids are stored in closed containers. [BCFC, Div. B, 22.214.171.124.(2)]
- Note: Closed container means a container sealed by a means of a lid or other device such that neither liquid nor vapour will escape from it at ordinary temperatures. [BCFC, Div. A, 126.96.36.199.(1)]
- Where the storage of flammable/combustible liquids are secondary to the principal activity, the limit of flammable/combustible liquids in closed containers that can be outside of storage cabinets is 600L, of which only 100L can be Class 1A liquid(s). [BCFC, Div. B, 4.2.8.]
- Individual storage areas are required to be separated by a minimum width of 2.4m [BCFC, Div. A, 188.8.131.52.(1)]
Suggested Safety Advice
- These storage units should be listed in the site owner’s fire safety plan, and any stored flammable liquids or hazardous materials should be identified by dangerous goods placards affixed to the exposed sides of the container to provide responders with information regarding hazardous contents.
- Fire departments should include in the pre-fire plan the content of such containers, their locations on the lot and proximity to combustible structures that may contribute to excessive heating of the storage unit should adjacent materials be ignited.
- The hazard must be recognised in the initial assessment of an incident and measures taken to isolate the hazard or modify firefighter suppression tactics. If there is flame impingement/exposure to any structure, container or vessel it should be investigated, assessed and monitored throughout the incident.
- To reduce the chance of injury to a firefighter from explosion, the use of unattended hose streams, and the firefighters distance from the storage unit should be considered if there is, or has been, significant direct or indirect heat applied to the container by the fire. These storage units or containers should be given the same consideration as pressure vessels when flammable or combustible liquids are suspected to be stored inside. Many of these containers are unable to vent when sealed and therefore greater exclusion zones should be maintained at weaker points of the containers, such as doors, where the container would be most likely to fail.
- Whenever possible the site owner or coordinator should be encouraged to provide some physical separation between these containers and combustible structures to prevent excessive heating during fire situations.
For more information about this bulletin, contact the Office of the Fire Commissioner.